Complete Wartsila 9 MWe Gas Engine Power Station for sale
This plant now sold but we have other gas engines here:
This plant was in operation until decommissioning in April 2009. All the equipment, including the buildings, was recorded to facilitate the re-build. This station is stored inside and will be sold either ex works or if preferred rebuilt and commissioned.
The picture shows the engine house bottom left, the cooling radiators middle right, and the gas input station far right.
Summary of parts
- Three Wartsila 3.0MWe 16v 25g gas powered 11,000 Volts generating sets
- Associated auxiliary and motor control panels
- Pumps, lubricating oil heat exchangers, and air compressors etc.
- Gas train
- 12 air blast radiators – four per generating unit
- Five panel 11000 volts switchboard
- 500 kVA station transformer
- Medium and low volt cables
- Control instrumentation cables
- Steel frame metalclad building
- 15 metre 3 way chimney
- Clean and dirty oil tanks
All within a steel framed metal clad and insulated building.
The plant has been operated and maintained by our associates in accordance with the manufactures instructions and schedules. They will, if required, reassemble the whole station, re-commission and, if appropriate, maintain and operate the plant.
ENGINES and ANCILLARY PLANT
The station was built in 1997. The three generating sets are individually housed in concrete cells providing a high degree of sound attenuation.
Component parts have decommissioned, labelled, protected and stored by our associates to keep the re-build cost to a minimum.
The units have been operated and maintained in accordance with the manufacturers instructions and are being thoroughly overhauled prior to re-siting. They are available for inspection in our associate’s works in Hereford
Specification and performance of each of three gensets
Gen Type: Wartsila W16V25SG
Engine Power: 3125kW
Rated output (ISO 3046/1: 3000kW
Swept Volume/cyl: 14.7 litre
Fuel input: 7317kW
Oil consumption: 1.7kg/hr +/- 25%
Generator rating: 3670kW
Protection/Insulation: IP23 Class F
Engine 1 hours run 60,301, ten thousand hour service at 53,620, five thousand hour service at 58,733 Engine 2 hours run 53,844, ten thousand hour at 46,399, five thousand hour service at 52,100 Engine 3 hours run 59,111,the ten thousand hour service was done at 53,09
MAIN ITEMS OF PLANT
Genset Control Panels
Individual two panel genset control and monitoring board with all control and power cables, instrumentation and protection.
Engine water and oil cooling circuits showing plate heat exchangers and exhaust silencers above. The engine cells are to the left off the picture.
MEDIUM VOLTAGE SWITCHBOARD
Five panel ABB 11000 volt switchboard with three genset incomers, one station transformer feeder and one mains outgoing breaker.
Battery charging panels [and mains protection panel in background]
24v and 110v battery charging panels
500kVA 11000volts/415volts DYn11 cast resin dry type transformer in main switchroom.
Mains protection panel is just in shot in the right foreground of the picture.
Power Plant Building
Building showing exhaust stack and cooling radiators.